1、 The stoker must operate the boiler with the use registration certificate issued by the labor department.
2、 The stoker who operates independently must hold the stoker's operation certificate and meet the requirements of the type and type of furnace.
3、 Before the ignition of the boiler, the main body of the boiler, combustion engine and other auxiliary equipment, all accessories, valves, water supply, oil supply system circuit and electric control department shall be inspected and confirmed to be normal.
4、 Open the air release valve and feed water into the furnace (the water level can be controlled by means of drainage after checking the water level and whether the alarm system works normally). The water level is slightly lower than the normal water level.
5、 Use "manual" to start the fan, purge the furnace, adjust the control system to "automatic" position, and then press the start switch, the boiler will follow the specified procedures: purging ignition combustion (large or small fire) - temporary shutdown. If there is a fault in the ignition procedure, the manual blower can continue to blow and then re ignite. If the ignition fails for three times, stop ignition and fuel supply. Find out the cause and eliminate the fault before re ignition.
6、 When the pressure in the pot rises to a little higher and the air pressure, the air valve can be closed when steam comes out of the air valve.
7、 In the process of boiler pressurization, the gas supply or boiler combination can only be carried out after the inspection and operation are confirmed to be normal according to the specified requirements.
8、 After normal operation, oil supply, air supply and water supply (except for full-automatic boiler) shall be adjusted frequently to keep water level and air pressure stable, adapt to load demand and ensure steam supply.
9、 Patrol inspection shall be conducted every hour during operation, and all records and signatures shall be made according to regulations.
10、 Each shift shall flush the water level gauge and discharge the sewage once, the safety valve exhaust test, the pressure gauge flushing water storage elbow and the verification of various safety protection devices shall be carried out according to the specified requirements, and the records shall be filled in truthfully and signed for approval.
11、 When the boiler is shut down normally, the air supply should be stopped first, and then the air supply should be stopped to keep the water level higher than the normal water level.
The most important thing to buy products is quality, and choosing merchants is honesty. Shandong gas boiler sincerely provides excellent services for customers. Welcome to visit our website: http://www.0577gf.com Below message consultation